Medium to high load capacity hangers designed to carry 2 or 3 trusses. Accommodates right or left hand hips (at 45-degree skews) and can be used for terminal hips with or without the center common jack. The MTHM-2 accommodates 2-ply hips or jacks.
Use all specified fasteners. See General Notes.
All multiple members must be fastened together to act as a single unit.
Shall be attached to a double girder truss to allow for required minimum nail penetration. With single 2x carrying members, use 10dx1 1/2" nails with 0.67 of the table values.
Right or Left Hand Hip Installation (Two Member Connection)
Terminal Type Installation (Three Member Connection)
Allowable loads have been increased for wind or earthquake loading with no further increase allowed; reduce where other loads govern.
Roof (125/160) is a download rating.
Tabulated hip and jack allowable loads assume that 75% of the total load is distributed to the hip and 25% to the jack. It is permitted to distribute 65% to 85% of the tabulated total load to the hip, and the remaining percentage of total load to the jack. The combined hip and jack load may not exceed the published Total Load.
For terminal hips divide the total allowable load by 2 to determine the allowable load for each hip.
Hip loads are for each hip.
Load distribution is 40% of total load for each hip and 20% for the jack. Other hip/jack load distributions are allowed if the sum of all three carriedmembers does not exceed the total load and the hip members are equally loaded.